POMPE DE CALDURA, AER CONDITIONAT, CHILLER
FOCS-ME 1001 – 9604
Condenserless unit Cooling capacity 219 – 2240 kW
- B – Basic
Compactness in terms of overall size and weight, helping installation and working on site
Adaptability at the building’s cooling request thanks to the continuous capacity regulation, assured by sophisticated control’s logic.
- WIDE OPERATING RANGE
Extensive range of operation with remote condenser operating up to 46°C air temperature
- SILENT OPERATION
Extremely silent operation thanks to the accurate unit’s design. Optional integral acoustic enclosure, reduces more the sound level beyond the best on market
- Integral acoustical enclosure (type base or plus)
- Electronic expansion valve
- Soft start
- Set-up for remote connectivity with ModBus, Echelon, Bacnet, Bacnet over-IP.
- Remote control keyboard (distance to 200m and to 500m)
- W3000SE Large
The W3000 SE Large controller offers advanced functions and algorithms. The keypad is generously sized with full operating status display. The commands and detailed LCD display make access to the unit’s settings easy and safe. These resources allow to consult and intervene on the unit by means of a multi-level menu, with selectable language setting. The diagnostics includes a complete alarm management, with the “black-box” and alarm logging functions for enhanced analysis of the unit operation. For multiple units’ systems, the regulation of the resources, via optional proprietary devices, can be implemented. Energy metering, for both consumption and capacity, can also be developed. Supervision can be easily developed via proprietary devices or the integration in third party systems by means of the most common protocols as ModBus, Bacnet, Bacnet-over-IP, Echelon LonWorks. Compatibility with the remote keyboard managing up to 10 units. Availability of an internal real time clock for operation scheduling (4-day profiles with 10 hour belts). The regulation features the continuous modulation of capacity, based on a dynamic dead band and referring to the leaving water temperature. As alternative, step-wise regulation is also available, referred to the return water temperature with selectable proportional- or proportional-integral logic.